Full Kit - XE COMBI Boiler 110K BTU State Proline [ Natural Gas ]
This kit includes everything you will need to hook up your boiler to your new Hug Hydronics System, this kit contains: Your Boiler, RIB, Fitting's kit, and the Combi Adapter kit.
You can find more information about the items below!
The 110K BTU Combi boiler will 3.5 gallons per minute of hot water for your showers and your floors.
The ProLine® XE Combi Boiler provides high efficiency space heating and domestic hot water (DHW) in a compact footprint that is easy to install and maintain. The efficiency of the Combi is rated at 95% AFUE (Annual Fuel Utilization Efficiency) making it available on many utility rebate programs. Lastly, the plain text Setup Wizard on the Smart Control LCD display will make installation a breeze.
The SCB-110H-P indoor residential Ultra-Low NOx Combi Boiler uses up to 110,000 BTU/hr of Liquid Propane to deliver a continuous supply of hot water and space heating for a home in high altitude regions. This High Efficiency heating system has a 95% AFUE and is ENERGY STAR Certified.
This solid state relay is very handy for coordinating any outside devices to run when the HUG Hydronics in-floor heating system is running.
It's conveniently mounted in an enclosure. 10 amp, SPDT, with a coil that can be driven at 10-30VDC or 120VAC. Model RIBU1C by Functional Devices, Inc. [datasheet]
The Fittings Kit:
Included with every Boiler when you buy our Hydronics system is a set of fittings and the installation guide and spec sheet.
The Combi Boiler Adapter:
The State Pro Line XE COMBI Boiler;s needs an adapter to work the HUG Hydronics In-Floor Heating System. This is that adapter. Now, with one huge COMBI Boiler, you can heat your house and your hot water with the same boiler.
* Installs with 1 tool, about 5 minutes of work.
How does it work?
The State Pro Line XE's have a pressure sensor which our adapter replaces with a low water level sensor and air remover. The probe senses if the water is low. If it is it sends a signal to the purge pins to run the pump 3 seconds, raising the water level enough to purge any air.
The water sensing probe gets stuck down a tube on the top, and the power cord goes down a hole and plugs into the circuit board of the COMBI Boiler. On the HUG Hydronics Tanks the black box slips in next to the thumb screws on the back. A hose goes into the tank and a connecting cord feed to the control board and plugs into the purge pins of the heater pump (usually pump #10).
Proline XE Combi Boilers